|This section covers installing the controls for the combined solar
water and space heating system.
Installing the Collector Loop controls...
Installing the Radiant Floor Loop controls...
Installing the Backup Heater controls...
|An off the shelf differential controller is
used to turn the collector loop pump on when the collector is hotter
that the water in the tank, and to turn the pump off when the collector
cools to the point where it is no longer heating the water.
Most commercial differential controllers come with a whole array of other features such as: displaying collector and tank temperatures, setting maximum storage tank temperatures, pump short cycle protection, vacation settings, ... and more. You can download the manuals from the suppliers of these controllers, and review the features and see what you think you need or want.
I'll pass on that I have our controller mounted in the bathroom, and
I do look at the temperature displays for the collector and tank and
find these helpful. I also have the maximum tank temperature set
to around 165F to increase the life of the EPDM lining. I think
its is also helpful to be able to set the difference in temperature
between the collector and the tank that causes the controller to turn
the pump on. That said, I have used very simple differential
controllers that only cost about $50 that did just fine -- so, this is a
place you can save some money if the budget is tight.
Installing the Differential Controller
You will want to follow the instructions for the particular differential controller that you buy, but normally the install will consist of four steps:
John Canivan and Richard Heiliger at the
offer a kit or assembled differential controller at a lower price.
This Shem 32 is another imported possibility. I've been using one of these on my Solar Shed system for this winter, and it has been fine. Features similar to the Steca and Caleffi. Price is attractive.
And this interesting myDTC one that looks kind of formidable, but does some logging -- would like to hear from anyone who has experience with it.
If you are using a PV driven pump, Guy Marsden offers a differential controller for PV systems ... As does IMC (listed above).
This shows how the connections are wired for the Steca controller I had earlier. The two orange wires go to the collector and tank temperature sensors. The black wire is the controller line cord that plugs into a wall outlet. The pump lugs into an outlet on the controller just to the left of the black cord.
There are a couple choices on the radiant floor heating system controls.
One straight forward system uses two thermostats in series. The first thermostat senses the solar storage tank temperature, and turns "on" when the solar tank water is warm enough to provide heat. The 2nd thermostat senses the room temperature, and turns on when the room is cold enough to require heat. So, when both thermostats are "on", the radiant floor circulation pump is activated, and the hot water from the solar tank is pumped through the floor loops.
This is the type of system I used on the Solar Shed heater project and is explained in more detail there.
If you want to use this kind of system but would rather use a regular programmable home heating thermostat rather than the Johnson A419 thermostat I used, this is relatively easy to do. Just have the home heating thermostat control a 24 VAC relay that switches the power on the pump line, as is done in the system described just below.
Since we added backup heating to our system, I am using a simpler system that eliminates the 2nd thermostat of the two mentioned above. That is, there is just a regular furnace style programmable room thermostat that activates a 24 VAC relay to turn on the pump that circulates heated solar water to the floor. The 2nd thermostat that senses solar tank temperature is dropped because the backup heating system insures that the tank is always hot enough to provide heat. The diagram for this system is shown below.
There is actually some merit in retaining the 2nd thermostat that senses tank temperature and keeps the pump from turning on if the tank temperature is too low to heat. The benefit would be that if something went wrong with the backup heating system, the 2nd thermostat would keep the radiant floor pump form staying on indefinitely trying to heat the floor with water that is too cool to provide heating. My thinking in taking the 2nd thermostat out was that we would soon notice the lack of heat and find out what the problem was and fix it.
The diagram below shows how the controls for the radiant floor heating work after the new backup heating system was installed -- this is what the system is currently running with, and it has been working fine.
When the room temperature drops, the room thermostat switch closes and activates the 24 VAC relay, which in turn powers up the floor loop circulation pump.
The 24 VAC is used because it is the standard for HVAC equipment including the room thermostats. All the parts are standard and easily obtained.
This shows the electrical connections in more detail.
The diagram shows more detail on the wiring connections.
A backup heater was added to this system in 2013 so that the solar system could take over the full task of heating the house. For the full explanation on the backup heater and how its designed, installed, controlled, and plumbed go here...
Gary February 12, 2011, December 21, 2013